Doubt the connector is your only problem. How old is unit and what brand is it. Most hvac shops can order compressors by serial number, model number, and make. Filter drier will have to be replaced, usually when compressor goes it ruins the "freon". What type does your unit use, is it r22, or 410. They don't make 22 anymore. Bad news, compressor is the most expensive part. If you replace yourself double check ordered part for line sizes, depending on make big line should be 3/4(maybe 7/8), small line should be 3/8. You have to be licensed to mess with the gases and in most places licensed to solder. You will probably have to have a tech replace to get any kind of warranty.
Most driers only flow one way, yours needs both because heat pumps pump both ways.
To view links or images in signatures your post count must be 10 or greater. You currently have 0 posts.
Amish washing the buggy^^^^
Last edited by traitor08; 03-22-2011 at 10:49 PM.